Stratos Elevator finished installing whisper-flex cable and buffer springs in the pit and they are currently mounting the hall call stations, as well as installing the tape leveling switches and readers for Elevator #4.
They finished mounting equipment and tape selector on top of the cab for Elevator #7.
Zimmer continues patching walls and painting on the 5th Floor.
The contractor continues framing the new walls in the 5th and 6th Floor lounges.
The contractor continues the installation of fan coil units, while the insulation sub-contractor insulates the piping.
Demolition of the interiors spaces in the 3rd and 4th Floor annex continues.
LSUHSC Facility Services continues installing locksets on Floors 3 and 4 and working on maintenance items throughout the building.
Perimeter Fence Project:
The sample of the pre-cast concrete for the decorative fence posts was approved by LSUHSC and is now in production.
Campus Roof Replacement:
Needham Roofing continues work on punch-list items and is applying sealant to the newly installed umbrellas around the bases of the exhaust fan supports.
The contractor continues with the electrical rough-in work.
Auditorium A&B Renovations:
The electric sub-contractor continues to remove old electrical and telecommunications wiring.
The contractor is installing new HVAC piping and drain lines.
The LSUHSC electricians continue roughing in and routing wiring for wall switches.
The contractor started furring out the media room walls where the monitors will be located.
Auxiliary Enterprises continues organizing and routing data wires.
Clinic Building Permanent Repairs and Mitigation:
Crews continue installing sheetrock and insulation on the 7th Floor.
The mechanical contractor is piping in supply and return mains to VAVs on the 6th Floor on the Bolivar St./Gravier St. side of the building.
Ductwork is being installed on the S. Prieur St./Gravier St. side of the 6th Floor.
Plumbers are routing medical gas lines to the new simulation rooms.
The hot water lines on the 6th Floor are being insulated.
Plumbers are working on the waste line for the bathrooms on the S. Prieur St. side that runs between the 5th and the 6th Floor.
Electricians are running copper cable from the Entergy vault to the new switchgear.
Crews are installing sheetrock and framing on the S. Prieur St. side of the 6th Floor.
They are also framing in the chase wall in the bathrooms on the S. Prieur side.
The contractor continues relocating sprinkler heads and installing HVAC grilles and return grilles.
Floor Lobby Renovations:
The contractor completed debris removal.
Floor Ceiling Removal:
Approximately fifty percent of the sprinkler heads have been moved to their new layout location.
The new corridor ceiling lights were delivered this morning.